The floorplan offers a virtual view of the facility and provides visual, color-coded guidance on the power utilization of the circuits installed within your cabinets. This allows you to see where capacity may be available to install additional equipment, or where it may be necessary to reconfigure or upgrade a circuit. Cabinets are colored according to the following criteria:
No power circuits are installed in the cabinet or the site does not yet offer circuit monitoring
All individual or primary/redundant (A+B) paired circuits installed within the cabinet are using less than 60% of their rated power capacity.
At least one individual circuit or A+B circuit pair in the cabinet is using between 60% and 80% of its rated capacity.
At least one individual circuit or A+B circuit pair in the cabinet is using over 80% of its rated capacity.
After selecting a cabinet, a menu appears allowing you to view the Power Usage page, create a support ticket, or view the assets installed within the cabinet.